Electrical portion of shut-off valve has an explosion-proof structure and is compatible with almost all disaster prevention systems.
Battery with built-in controller can back up the operation in case of power outage.
Optional specification of one controller with two shut-off valves is available.
32 combination systems are available.
Lock after shut-off must be manually released.
|Model||MEV (Lift type)|
|Operating pressure||Less than 1.0 MPa|
|Adjustable pressure range||OPS-L type: 1.96 to 19.6 kPa OPS-H type: 17.7 kPa to 0.785 MPa
UPS-L type: 0.49 to 14.7 kPa UPS-H type: 9.81 kPa to 0.637 MPa
|Material||Valve: Main unit [FCD], and main portion [SUS]
|Scope of system||Over pressure shut-off (OPS), under pressure shut-off (UPS), remote shut-off, alarm-linked shut-off (gas leakage, earthquake, and fire alarms)|